Entergy: Third-party analysis confirms cause of Super Bowl outage
Contributor: FOX8Live.com Staff
New Orleans, La. -
Entergy says an independent analysis has confirmed that a faulty relay device caused the Feb. 2 power outage during Super Bowl XLVII. The report also lists several contributing factors, including inadequate communication between the manufacturer and the utility.
FOX 8 received this news release from Entergy New Orleans Thursday afternoon:
An independent, third-party forensic analysis commissioned by Entergy New Orleans, SMG and the Louisiana Stadium and Exposition District to investigate the cause of the partial power outage during Super Bowl XLVII has confirmed that the cause of the outage was the "misoperation" of a relay device. The analysis was performed by Dr. John A. Palmer of Palmer Engineering & Forensics.
Highlighting what he characterizes as a "design defect" in the relay, Dr. Palmer's report states on page five, "Behavior of the device in a manner contrary to the published functionality of the device constitutes a design defect."
Dr. Palmer's report identifies the primary cause of the power disruption and three contributing factors. They are as follows:
1. The cause of the outage was a misoperation of the relay.
2. A contributing factor to the misoperation of the relay was the unstable operating condition of the relay around the set point of the subject relay, which was a design defect.
3. A contributing factor to the outage was the inappropriate setting of the relay, which was the factory default setting.
4. A contributing factor to the inappropriate setting was inadequate communication between the manufacturer and the utility.
The relay device, which is located in a vault outside of the Mercedes-Benz Superdome, was a component in the switchgear that was placed into service in December 2012 after being inspected, tested, and commissioned by the manufacturer. The relay was taken out of service following the Super Bowl. In addition, Entergy New Orleans has confirmed that there are no other such devices installed elsewhere on its system.
"We are pleased that Dr. Palmer's independent analysis has verified the root cause of the outage and confirmed that the relay operated in an unintended and unpredictable manner," said Charles Rice, president and CEO of Entergy New Orleans. "It has been our objective all along to identify the cause of the outage, learn from it, and prevent such an occurrence from happening again. The device has been permanently removed from service."
SMG, which manages the Mercedes-Benz Superdome, released this statement in response to Entergy's report:
We are pleased that this report
has conclusively determined that the root cause of the outage was a defective
relay device manufactured by S&C and located in Entergy's vault, and that
the Superdome's own power system was not the cause of the outage. Entergy has
reassured us that the faulty relay has been taken out of service and that
systems are operating normally. We are confident that the problem has been
corrected. We appreciate Entergy's swift response in completing this analysis
and their commitment to ensuring a continued seamless power delivery system for
The national director of the Deaf Federation of South Africa says a man who provided sign language interpretation on stage for Nelson Mandela's memorial service, attended by scores of heads of state, was a...more>>
As one world leader after another paid homage to Nelson Mandela at a memorial service, the man standing at arm's length from them appeared to interpret their words in sign language. But advocates for the deaf say he...more>>
An old country road outside Mandeville, has seen a doubling of traffic accidents and huge delays since an interchange with Interstate 12 opened up. The state has come up with three proposals to makemore>>
An old country road outside Mandeville has seen a doubling of traffic accidents and huge delays since an interchange with Interstate 12 opened up.more>>